Newbourne 40FS stove
The Newbourne 40FS is the smaller version of the Newbourne 50FS stove. It is DEFRA approved from smoke control areas. The Newbourne 40FS has great controlability with both the primary and secondary air controls.
- Height: 580mm
- Width: 503mm
- Depth: 374mm
Most Recent Review
Stove expert replied: Purchasing the same stove again is a good recommendation for any stove, great comments.
Most Popular Review
it gets a bit annoying ,I didn't get that with our old burner.
Stove expert replied: Is the flue lined? Does the air flow noise continue if the controls are fully shut? It may be that the flue draw is excessive for this stove!
More reviews for Newbourne 40FS stove (page 1 of 2)
Stove expert replied: You do not say how old the product is, if under 12 months I would advise that you go back to your supplier to see if this can be addressed under warranty. A longer lasting fix might be to use graphite powder on the moving part, it may need this again in the future if no obvious way of loosening the slider is evident. Graphite powder is not affected by heat whereas WD40 will be. Does this only happen when the stove is hot?
Stove expert replied: More information is required to be able to advise fully. You haven't said if this is a new installation, if the chimney is lined and if it has been swept, what fuel is being burnt, if there is a room vent etc etc. Sometimes you can get a smell but generally it is when the stoves paint is curing when new, if the chimney needs cleaning, a down draught and there are other causes so I would suggest further investigation to establish the cause and then you should be able to find a remedy that is suitable.
t feel right for some reason...
Stove expert replied: Have you gone back to your supplier? This may be a change that has been made and often a manufacturer provides a glove for opening the stove due to the handle getting hot.
Stove expert replied: The internal liners can continue to be used if they are cracked providing they are protecting the metal of the stove. If they have become damp they will deteriorate more quickly and care when loading the stove is important not to heavily impact them with the fuel if possible. They are not covered by warranty as deemed as consumable. You could try reversing the ones that are showing most wear so that you can use the stove and purchase replacements when required. Both faces can normally be used.
new flue liner down.Please can you advise.
Stove expert replied: The flue may have an excessive draw on it and you may need to have a damper or stabilizer fitted to gain better control of the appliance. This requires further investigation, as a matter of urgency, as leaving it burning too vigorously can lead to permanent damage to the appliance and will invalidate the warranty.
logs last longer. Seems very efficient. Any noise when the air intakes are open disappear as soon as they are partially closed. The large glass window gives a perfect view of the flames and the heat output is phenomenal. The only minor niggle for me is the various nooks & crannies below the grate & in the back of the door where ash accumulates but use of an ash vacuum cleaner solves this. Great choice of stove for us.
Stove expert replied: Good review. It is paramount that the fuel used is dry and seasoned and has a moisture content of less than 20% not only for the heat that is generated but to maintain a clear flue.
into the fire when it is burning? Already spent £90 for 2 replacements so quite frustrated that this is happening. Please can you advise why and suggest what we can do to prevent it? Thank you. Also the glass has a foggy, white look which does spoil the effect a little.
Stove expert replied: The glass discolouring with a white milky shadow is normally caused by the stove over-firing, this may be down to operator error or an over -drawing flue. If the stove is not controllable, so that you can achieve a gentle flame picture, then the flue draw should be taken and if it exceeds the manufacturers guidelines this needs to be rectified. Either a flue damper or stabilizer is required to prevent further damage. The top brick breaking 3 times in such a short space of time may indicate an over-drawing flue and if you get this corrected the problem may be resolved.