Hunter Herald 8 stove
The Hunter Herald 8 stove is available with a high canopy, low canopy or with a flat top.
The Herald 8 comes as a wood burning model or as a multi fuel and can be fitted with a backboiler.
There is a double sided version of the Herald 8 available as well.
- Height: 624mm
- Width: 635mm
- Depth: 434mm
- Flue Diameter: 150mm
- Fuel: Multi fuel
- Efficiency: 78.9%
Most Recent Review
I have had to replace the grate on my stove twice now, the last one warped and the rung broke through after just 2 seasons use. Hunter said that I must be burning the wood at too high a temperature... [ read more ]
Stove expert replied: When you close the vents down do the flames die down or stay busy? If they stay busy please check the door seals of the stove and the flue draw to insure that the draw is not excessive. If it is greater than recommended by the manufacturer the stove will be exposed to higher than normal working temperatures and internal parts will fail prematurely. As you have a grate this is a multifuel stove and the ash will be harder to build up which is what you need for efficient woodburning. This may not be a failure with the stove but an installation problem that needs further investigation.
Most Popular Review
We bought our Hunter multifuel stove 5 months ago and we wouldn't buy another. We were told it would heat our entire downstairs, 2 large reception rooms, a large hall and kitchen. Whilst our... [ read more ]
Stove expert replied: A room heater is what it says and if there is only a door way between spaces then the radiant heat to this space may not be that great. It will obviously raise the temperature but may not be man enough for full heating. Open plan spaces are much easier to heat from one appliance.
More reviews for Hunter Herald 8 stove (page 1 of 4)
Bought the Hunter Herald 8 some seven years ago to heat a large conservatory. It is very effective and has a strong updraught, until the door is opened to refuel.Then it sends puffs of smoke... [ read more ]
Stove expert replied: If this is a single height flue system then this can possibly contribute to the smoke coming back into the room when the door is opened on the stove, is there an air brick in the room? If there is any single flue pipe on the system this can lead to condensation in the flue due to the fast cooling of the gases. A salty environment will also not be good for any stove and flue system.
We bought this fire 12 months ago having previously had a gas stove. It has taken me 12 months to really get the balance right in terms of burning wood and getting the most heat out of it. It... [ read more ]
We were told it would heat radiators, hot water and the lounge where it's fitted, it struggles to heat the lounge never mind hot water or radiators. The engineer who installed has been back so many times it's unreal. We burn good wood, Oak. We cannot open the doors without choking to death, the smoke billows out, before anyone tries to tell me why, we've tried it all. The chimney is so high I need a light on the top for aircraft. It needs to be blazing to get any heat out of it at all but you are putting logs on the size of shoe boxes every 5 minutes. Go for a fire like Villager with a boiler at the top. This stove is going in the skip.... [ read more ]
Stove expert replied: Was the stove sized correctly for the system that you are wishing to run? If the stove is too small then it will struggle to heat a large system. These stoves are tested so that the outputs stated are achievable providing it is installed and used as per the manufacturers instructions. It seems contradictory the have smoke coming back into the room when you open the door (down draught indicating a poor draw on the flue) and then to say that you are feeding the stove with fuel every 5 minutes (more likely to indicate an over drawing flue making the stove work very hard but not producing much heat). Have you an airbrick in the room? It does seem that the installation needs to be checked fully to ensure that all aspects are correct as indicated in the manufacturers installation manual.
Bought my Herald 8 slimline in December 2015 after 2 months the door seals began to disintegrate. After contacting Hunter stoves and getting into a long email conversation with a lady I was... [ read more ]
Stove expert replied: Any warranty issues that occur during the warranty period should be dealt with by the stove supplier in the first instance, as this is who you have your contract with. They will then deal with the manufacturer to get this rectified on your behalf. It is not clear why this procedure was not followed from the above. It is a shame that you have had to wait for the replacement parts and found that the brackets were not originally supplied, quality control is taken seriously by stove manufacturers and I am sure that following this being bought to Hunters attention, improvements will be made to prevent similar from occurring in the future.
Hi I have a hunter 8 that's connected to a boiler to heat my radiators but it seems to take forever to heat the house and the radiators don't seem to get very hot Is this normal ?
Stove expert replied: Boiler stoves can work well and effectively but the installation is key, second is the fuel that you are using. You will only get out of a stove what you put in so the fuel needs to be of good quality - if wood with a moisture content of less than 20%. Smokeless fuels will provide a good heat source and a prolonged heat due to their construction. Make sure the fire box is well stocked, just putting the fuel in the middle will not get a heat transfer to the water jacket. The output of the stove is also paramount as it needs to match the requirement of the system as if not sized correctly it may not be big enough to drive the system effectively, was this checked before installation by a qualified heating engineer?
I had the Hunter Herald 8CE installed 3 months ago by a Hetas engineer along with a new lining and an anti-downdraught chimney cowl. I've found that the updraught is far too strong and even... [ read more ]
Stove expert replied: The air controls should make a difference when operated and if not the top one can sometimes not be in the correct position. the deflector on the underside of the Top Air is removed and check that the slider is sitting over the top air plate with the gasket in place properly? The slider may not be aligning up with the holes properly causing a leakage of air even when the plates are supposed to be closed? Worth checking this perhaps.
Just replaced top air control which was a nightmare in itself but still fire not working efficiently and when closed down fire still draws. Not happy particularly as this is a replacement as... [ read more ]
got my herald 8 with a boiler fitted. I notice there is no baffle plate and just assumed that you don't have one when a boiler is incorporated? Whatever, the thing works perfectly and adds so... [ read more ]
We bought the Herald 8 with wrap around boiler for our old cottage to replace expensive LPG. The stove was installed to spec and connected up to our existing (modern) radiators. Like many of... [ read more ]