Broseley hercules 20B
The Hercules 20B is a high output boiler stove
Most Recent Review
We had the Hillandale Hercules 20b fitted in our new build 2 years ago it a great burning fire but because the house is so well insulated the house gets too warm to quick is there a way that... [ read more ]
Stove expert replied: If the boiler is too large there is little that can be done to make it produce less other than the operating the controls on the stove itself. Perhaps using it for shorter periods at a time may help the situation, it will not do the stove much good to be shut down all the time so shorter periods of a faster burn will be more beneficial.
Most Popular Review
works well gets water hot very quick ie. full tank about 1.5 hours (65degC) airwash poor. air vents poor finish, apart from these, very happy with the stove.
More reviews for Broseley hercules 20B
Having problems with smoke back tracking in to room every time we open door of stove to put wood on. Have cleaned the chimney and cleared the baffle tray, I am at a loss what problem could be, becaues it has been working fine in the past , has any body got any ideas please.... [ read more ]
Stove expert replied: It may be due to weather conditions or the baffle being slightly distorted or not back in the correct position. If you have altered anything in the house (eg Double glazing perhaps) this can affect the way a stove will perform. If you are surrounded by trees may also effect the stoves performance and further investigation is recommended. Adding an anti-down draught cowl may solve the problem and may be worth further investigation.
Having same problem as other reviews lots of heat to room none to water also fitted by hetas fitter who advised plumbing and flue not a problem. Could anybody help with this problem.
Stove expert replied: Have you contacted their Technical Department for advice.
Please can someone advise? The Broseley gives lots of heat to the room but not to the heating or water. Has anyone else had this problem? Fitted by Hetas fitters and they say not problem... [ read more ]
Stove expert replied: Does the stove appear to be working well or burning hard and not very controllable? If the flue has a strong draw then it could be that much of the heat is going up the flue rather than into the water. Needs further investigation.
The best thing we ever bought for our draughty Yorkshire Farmhouse. We have had it for 12 months and the house has never been as warm. Invest a small amount in a cheap moisture meter to ensure... [ read more ]
We have had this fire for three years. We keep it in 6-7 months at a time without letting it go out. We burn wood during the day and a bucket of Burn Well(nuggets) at night which easily keeps... [ read more ]
Stove expert replied: Smokeless fuels tend to be cleaner burning on the glass and it is worth trying various types before buying in bulk as they do vary with different models.
We bought the Broseley Stove Herculees 30kw last year, it is supposed to heat around 24-26 rads, however we had the stove fitted connecting it with a nutriliser to our Gas boiler so that the... [ read more ]
Stove expert replied: Ensure Qualified Hetas Engineers install the appliance and secondly try different fuels until you find the one that works best on your appliance and you get a warm outcome.
Generally works very well but took time getting to know the settings when in use. \n
The b20 is a great looking stove but I am having problems getting the water and rads hot. I've got a great fire, the thermosat on the steel pipe is showing 300, the water and rads are luke warm... [ read more ]
Stove expert replied: I suggest getting advice on the heating system that has been installed as it sounds as if the heat is not getting away from the stove to where it should be (cylinder and radiators). The installation is critical on boiler stoves and there may be a simple explanation why this is not performing as expected.